Everglades National Park
Venergy was selected to take on the task of running 700' of underground electrical utilities from a service transformer to a newly built camp site shower house. Three 700 mcm alumium conductors and a 3/0 copper ground conductor where ran through 4" PVC schedule 40 conduit, and connected with insulated multitap connectors, with 3M detectable buried tape. A new 400 amp service panel was installed replacing the previous aged 200 amp service disconnect. Excavated between 24" - 36" through coral rock and limestone with a special purpused trencher to be able to lay the PVC are the correct depth.